If the word order is wrong then typically floating-point values such as temperature readings are received but the values make no sense.
In that case, go to Studio / Modbus / Device definitions and change the setting for Wordswap for the respective device, save the table and restart the NETx Server.
Article applies to the following products:
- NETx BMS Platform
- NETx Multi Protocol Server
- NETx BMS Server 2.0