NETIP_TUNNELING_SOCKET; Received Telegram: <KNX-group-address>@<IP-address> from <KNX-phys-address> has different data size as defined (defined:<x>, received:<y>).
|Related Products||BMS Server 2.0, BMS Platform|
|Description||The BMS Server has received a telegram from the field that does not match the respective definition regarding the length of the data.|
|Causes||The expected data size as defined in KNX / Telegram definitions does not match the received number of octets as sent by the device.|
|Resolutions||Make sure the group address is properly configured in the ETS and choose a matching data size and type in KNX / Telegram definitions.|